Fountain equipment maintenance personnel management:
Professional training for fountain equipment maintenance personnel, electrical equipment maintenance personnel should also hold professional certificates; Every six months to assess the fountain operators, strengthen the use of management.
Installation of fountain equipment
1. Fountain cables must be connected without water and protected with three layers of waterproof tape, insulating tape and high-voltage insulating tape.
2. The replacement of the fountain underwater lamp must be carried out without water and the bolts should be tightened firmly.
Inspection of fountain equipment
Inspection of underwater lamp: the underwater lamp of fountain should be checked and tightened once a month to avoid short circuit fault caused by water in the lamp body.
Cable inspection: semi-annual inspection of cables not in water to check the aging condition and avoid unnecessary losses.
Inspection of sprinkler head: in order to ensure the beauty and consistency of fountain water, reset sprinkler head with changing Angle at any time. It is forbidden to use sharp objects to knock it back to prevent damage of sprinkler head.
Fountain electrical equipment testing: fountain electrical equipment should be maintained regularly, six months to the cabinet of electrical equipment vulnerable to detection level to do necessary maintenance; The maintenance and overhaul of electrical equipment should be carried out under the condition of cutting off the power supply. If live operation is needed under special circumstances, safety protection measures should be taken and special personnel should be set up to monitor the important parts.
Replacement of fountain equipment
1. The standby fountain equipment shall be started and operated regularly (change it every day with high use frequency, and change it once with low use frequency) to prevent degradation of equipment performance.
2, the solenoid valve diaphragm replacement should be removed in the pipe objects all dry static; Tighten screws in diagonal order.
3. Computers and programs are upgraded once a year.
Cleaning of fountain equipment
Fountain water pump cleaning: the fountain water pump suction mouth should be cleaned every month to prevent dirt blocking the suction mouth, reduce efficiency and even cause equipment damage. The submersible pump must release the cooling water during the winter shutdown to avoid freezing damage to the pump body. The oil-cooled pump needs to close the valve.)
Fountain piping cleaning: once a year. Water should be drained from the pipes before the fountain equipment is out of service in winter to prevent the pipes from freezing and cracking.
Cleaning fountain nozzle and underwater lamp: once every half a year. Pay attention to nozzle riser and underwater colored lamp during cleaning to prevent damage.